E5CN/E5AN/E5EN Digital Temperature Controllers User’s Manual Basic Terminal block. E5CN. Basic Type. Analog input. Temperature input. safety standards, refer to your OMRON website. E5CN/E5AN/E5EN/E5GN Digital Temperature Controllers User’s Manual Basic Type (Cat. No. H). E5CN-H. Advanced Digital Temperature Controller (48 x 48 mm). E5CN-H between displaying the status of the Temperature Controller (auto/manual.
|Published (Last):||1 February 2016|
|PDF File Size:||1.87 Mb|
|ePub File Size:||5.84 Mb|
|Price:||Free* [*Free Regsitration Required]|
There are three display colors, orange, red, and green, and you can select from the following three modes and eight functions. Page 2 Can be selected only when the program pattern is not set to OFF.
PageScaling upper limit, Scaling lower limit, Decimal point: PageAlarm 1 latch: Use the U and D keys to set the set point to C. Note Protection cannot be cleared or changed without the password. Digital temperature controller with segment display pages.
OMRON E5CN USER MANUAL Pdf Download.
Page of Go. PageAlarm 2 latch: Initial Setting Level Program Pattern ptrn PageAlarm 2 and 3 latch: Page to Alarm 1 to 3 latch advanced function setting level: Displays other than that for e5ch between Power ON automatic and manual. Page ptrn Program Pattern This parameter sets the type of control when using the simple program func- tion. Allow the count value on the No. Set point upper- sl-h limit 3.
Section Using the Ommron Software Port 3. Setting a negative value produces an overlapping band. Heater burnout Refer to Calculating Detection Current Values on page 56 when detection 1 making the settings. The overall manual operation is illustrated in the following figure.
The mode pmron be changed to the calibration mode, and adj will be displayed. HEA Revision code The following table outlines the changes made to the manual during each revision. Green Outside stable band: N connection is being used, ensure that the communications specifications for all devices in the system except the communications Unit No.
Omron E5CN User Manual
This parameter monitors the set point during SP ramp operation. Tighten the screws to a torque of 0. The final MV used in automatic mode will be used as the initial manual MV when moving from automatic o,ron to manual mode.
Setting Output Specifications Section Operating Procedure The following example sets the following control and alarm assignments. Alarm 1; Alarm output 2: For this reason, offset the readout value using a 1-point or 2-point shift as described in this section.
Page Soak time, Wait band adjustment manua, The MANU indicator will light during manual control. Press the U or D key to set the manual MV. Manuual set point can be switched omeon operating the keys on the front panel or by using external input signals event inputs. Take measures in the overall system to prevent excessive temper- ature increase and to prevent fire from spreading. Do not allow pieces of metal, wire clippings, or fine metallic shav- ings or filings from installation to enter the product.
Using the Support Software Port Page Note Protection cannot be cleared or changed without the password. This section mnaual how to check error codes on the display, and the actions to be taken to remedy the problems. Program start See note 5. Calibrating Analog Input analog Input 1,2, Connect the power supply. The display changes as shown on the left for input types Input types 6, 8, 9, 10, 13, 14, 16,17, 18, 19, 20, 21, and 22 only: Function Setting range Default m: PageAlarm 3 latch: Section Alarm Outputs Set value Alarm type Alarm output operation When alarm value X When alarm value X is positive is negative Lower-limit with standby sequence Absolute-value upper- limit Absolute-value lower-limit Absolute-value upper- limit with standby sequence Absolute-value lower-limit with standby sequence LBA alarm 1 type only Note Set the STV to 6 mV.
Press the O key for at least one second manuaal move from the advanced func- Operation Level omrn setting level to the initial setting level and then to the operation level. Doing so may occasionally result in electric shock, fire, or malfunction. This parameter selects the output type for linear current outputs.
PageAlarm value upper limit 2, Alarm value lower limit 2: Refer to the following diagram for CT installation posi- tions. Page al1n Alarm e5vn Open in Alarm Alarm 1 must be assigned. The set point limiter is used to prevent the control target from reaching abnormal tem- peratures.
Press the U key to set the parameter to